Provide excitation system for synchronous machine and regulate its terminal voltage in generating mode
Simscape / Electrical / Specialized Power Systems / Electrical Machines / Synchronous Machine Control
The Excitation System block is a Simulink® system implementing a DC exciter described in , without the exciter's saturation function. The basic elements that form the Excitation System block are the voltage regulator and the exciter.
The exciter is represented by the following transfer function between the exciter voltage Vfd and the regulator's output ef:
- Low-pass filter time constant
The time constant Tr, in seconds (s), of the first-order system that represents the stator terminal voltage transducer. Default is
- Regulator gain and time constant
The gain Ka and time constant Ta, in seconds (s), of the first-order system representing the main regulator. Default is
[ 300, 0.001 ].
The gain Ke and time constant Te, in seconds (s), of the first-order system representing the exciter. Default is
[ 1, 0 ].
- Transient gain reduction
The time constants Tb, in seconds (s), and Tc, in seconds (s), of the first-order system representing a lead-lag compensator. Default is
[ 0, 0 ].
- Damping filter gain and time constant
The gain Kf and time constant Tf, in seconds (s), of the first-order system representing a derivative feedback. Default is
[ 0.001, 0.1 ].
- Regulator output limits and gain
Limits Efmin and Efmax are imposed on the output of the voltage regulator. The upper limit can be constant and equal to Efmax, or variable and equal to the rectified stator terminal voltage Vtf times a proportional gain Kp. If Kp is set to
0, the former applies. If Kp is set to a positive value, the latter applies. Default is
[ -11.5, 11.5, 0 ].
- Initial values of terminal voltage and field voltage
The initial values of terminal voltage Vt0 (pu) and field voltage Vf0 (pu). When set correctly, they allow you to start the simulation in steady state. Initial terminal voltage should normally be set to 1 pu. Both Vt0 and Vf0 values are automatically updated by the load flow utility of the Powergui block. Default is
See the Hydraulic Turbine and Governor block.
Inputs and Outputs
The desired value, in pu, of the stator terminal voltage.
vd component, in pu, of the terminal voltage.
vq component, in pu, of the terminal voltage.
Connect this input to a power system stabilizer to provide additional stabilization of power system oscillations.
The field voltage, in pu, for the Synchronous Machine block.
 “Recommended Practice for Excitation System Models for Power System Stability Studies,” IEEE® Standard 421.5-1992, August, 1992.
Generic Power System Stabilizer, Hydraulic Turbine and Governor, Multiband Power System Stabilizer, Steam Turbine and Governor, Synchronous Machine SI Fundamental, Synchronous Machine pu Fundamental, Synchronous Machine pu Standard
Introduced before R2006a